1. The Introduction of The Clean And Efficient Air Outlet
Efficient air supply outlet is an ideal terminal filter device for the thousand, ten thousand and 100,000 level purification air conditioning system, which can be widely used in the pharmaceutical, health, electronics, chemical purification air conditioning system and other industries.Efficient air supply outlet is used as the terminal filter device for renovation and new 1000-300000 level clean rooms, which is the key equipment to meet the purification requirements.The efficient air outlet contains static pressure box, distribution plate, efficient filter, and the interface with the air duct can be top or side connection.
1). The efficient air outlet is an ideal terminal filter device of thousand, ten thousand, 100,000, and purification air conditioning system.
2). It can be widely used in pharmaceutical, electronics, chemical and other industries.
3). Efficient air supply outlet is the terminal filter device used for transforming and building clean rooms of class 1000-300000, which is the key equipment to meet the purification requirements.
Product profile: The efficient air outlet contains static pressure box, distribution plate, high efficiency filter, and the interface with the air duct can be top or side connection.
2. Size And Parameters Of Clean And Efficient Air Outlet:
3. The Feature of The Clean And Efficient Air Outlet
1). Clean rooms with various cleanliness levels and various maintenance structures.
2). Air outlet material: carbon steel, stainless steel, aluminum plate and plastic;
3). Roof supply for non-uniform clean room;
4). The diffuser has various forms, beautiful, flat and uniform in style.
4. Note For The Installation of The Clean And Efficient Air Outlet
Notes for the installation of clean and efficient air supply outlet:
1). Before installation, it is important that the size and efficiency requirements of efficient air supply outlet must meet the site design requirements of clean room and customer application standards
2). Efficient air outlet installation need to clean good products and clean room clean of comprehensive, such as purify the dust in the air conditioning system, should be cleaning removal, need to meet the cleaning requirements standard and interlayer or ceiling also need to clean, clean air conditioning system must be run continuously more than 12h, again clean treatment.
3). The safe transportation of efficient air supply outlet should be placed in strict accordance with the marked direction of the manufacturer, and violent vibration and collision should be avoided.
4). Before the installation of efficient air outlet, the packaging shall be inspected on site, including whether the filter paper, sealant and frame are damaged; whether the side length, diagonal and thickness meet the requirements; whether the frame has burr and rust (metal frame); whether the product certificate, and whether the technical performance meets the design requirements.
5). Conduct leakage detection of efficient air outlet, check and check whether the leakage is qualified, and the installation should be reasonably deployed according to the resistance of each air outlet. For unidirectional flow, between the filters on the same air outlet or air supply surface, the difference between the rated resistance and the average resistance of each outlet should be less than 5%.Efficient air level equal to and above 100 clean room.
6). The clean room needs to install the efficient tuyere turning side and the seam between the ceiling plate, remember that the cracks must be strictly treated.Avoid efficient air outlet damage or damaged coating shall not be installed, the installation of air outlet and air duct must be strictly connected, the opening end with plastic film and tape to reinforce the dense air treatment.The above matters needing attention we must carefully abide by the slightly wrong, is a direct impact on the whole clean room clean standards.
5. The Application of The Clean And Efficient Air Outlet
6. The Purchase Notes of The Clean And Efficient Air Outlet
The price of this shop does not include tax points, and additional tax points are required for billing. For details, please consult customer service.
▲ Shipping Instructions
The goods in this store are all large-volume goods, and the freight varies greatly in different regions. The goods do not include freight and wooden frame packaging costs. The actual freight is calculated according to the product volume, quantity, wooden frame (export wooden box) packaging, and delivery address. Before shooting, you must contact customer service to calculate the freight! In order to avoid unnecessary misunderstandings, directly photographed and not shipped, need to make up the freight and wooden packaging costs before delivery.
In order to protect your purchase rights and provide you with high-quality services, you need to be the logistics personnel when you sign for the package. It will help you to solve it properly and quickly (if there is no inspection and receipt, the store will not be responsible for any damage, small pieces and other reasons to return).
7. The Introduction of Dong Guan Zhuo Wei Air Purification Technology Co., Ltd.
Q1: What is you minimum order quantities?
A :Our MOQ is one set which can meet your sample requirement.
Q2: What is your leading time.
A :It’s based on your quantities and the sizes of the products.Generally it takes us 20 days for one container and 10 days for sample orders.
Q3: What is your payment terms?
A :30% by T/T as deposit, balance will be payed before delivery.
Q4: Do you accept OEM&ODM?
Q5: Why maxi?
1). 2 years warranty time guarantee
2). 24 hours to give you prompt and further information
3). Send invitation and arrange everything for you when you come to China